the formation instructions of diesel generating sets：
1. Diesel generating sets
all diesel generating sets include diesel engine, alternator and control box and all the alternators have been made by fujian fuan gangfa electrical machinery co, ltd.
2. Starting method of gen-sets.
a). Manual switch
b). Automatic starting wholly: when electric supply has been stopped, the gen-sets can start three times automatically in 3-28seconds(time can be adjustable)between electric supply and everytime need 6-8seconds. Lt will spend 12 seconds to accept load when electric supply is resumed, gen-set will maintain 23-230 seconds, then closes down automatically.
3. Control system
apparatus: voltmeter, frequency meter, amperage meter, voltmeter, voltmeter of battery, meter of water temp. , oil meter. Control section; starling handler, key type switch, inductive type self-protection switch, and indicator.
1． voltage stead-state regulation±1%fluctuation ratio1. 5%;
transient-state regulation-15~20% stead time 5s
frequency stead-state regulation5% fluctuation ratio1. 5%;
transient-regulation±10%stead time 5s.
2． he noise of gen -sets should be no more than 85db(a);
the fuel consumption is no more than 2. 5kg/kw. H.
remarks: all the diesel engine have been made in china.