The active parts of the transformer is placed in a closed tank at its upper part by a plugged cover. Lifting rings are fixed on the cover allowing the lifting of the cover and the oil-filled transformer. (50 mm diameter)
. The tank bottom is reinforce to allow the lifting with the (UPN)
.The tank is conceived so that to avoid any risk of water stagnation.