As water evaporates within a boiler, dissolved solids in the water are left at the bottom of the boiler, resulting in buildup of sludge and scale. This buildup is alleviated by discharging some boiler water through a valve at the bottom of the boiler. High concentrations of solids can also lead to foaming near the top of the boiler and result in water hammer, which may damage piping, steam traps, and process equipment.
|Capacity ||8 PTH|
|Pressure ||10.5 Kg/cm²|
|Feed water TDS||25 ppm|
- Blowdown required maintaining desire boiler water TDS 3500 ppm:
|Avg. Load ||140TPD|
|Req. Rate ||1007 Kg/day|
- The BBC 06 is suitable for a wide range of systems.
|Boiler Type||Both Vertical and horizontal boilers|
|Blowdown flow rate||Up to 4000 Kg/hr|
|Boiler Pressure||Up to 32 Kg/cm²|
|Required inputs||3 to 6 bar air line. 220V 50 Hz AC power line|